Housing: Epoxi/polyester powder-coated sheet steel
Diffuser: flat borosilicate glass with a high thermal and mechanical stability
Gasket: EPDM formed gasket
All-pole are disconnected via NC switch when glass cover is opened.
The light fitting is normally supplied without light sources, two Ex e cable glands M25, one Ex e plug
M25 and with two ring screw M8 (pendant version).
|Apparatus category:||II 2GD|
|Explosion protection:||Ex db eb mb IIC T4 Gb
Ex tb IIIC T80°C Db
|Enviroment temperature:||-30°C ÷ +50°C|
|Degree of protection:||IP66|
|Rated voltage:||220-240 V|
● T8 fluorescent lamps in parallel configuration
● Switch with safety lock; when opening the central lock, all poles of the volt-age supply to the ballast are disconnected
● In case of a lamp fault, the electronic ballast disconnects the defective lamp from the power supply
● Recessed mounting set for clear rooms